||Smart Power Distribution > Low Voltage > MCCB & ELCB
||Meta-MEC MCCB&ELCB Series
||We want to use your Meta-MEC MCCB breakers in our DB but we encounter this issue about the line and load side terminal of you breakers. Actually, we want our DB to have Bottom entry for our cables but as per the sample breakers shown to us by the local suppliers bottom side was the load side of the MCCB.
Question: Can we BACKFEED the Meta-MEC MCCB breakers, where the Line and Load are clearly labelled/marked at the upper and bottom side of the breaker respectively?
Unfortunately you can not use upside down. As you can see the mark on the MCCB cover, Line & Load side is determined for its quaility.
If you use like this, some accidents happened, it can't break & extinguish arc perfectly. it's not recommended... LSIS can't guarantee the quality.
But for the Susol series it is available.
thank you & regards
||I can’t connect XG5000 to XBE-DR30E(CPU V1.00).
Could you inform me how to update the CPU version?...
||How to Communication between GIMAC - II Plus VS I4XS4UE
GIMAC - II Plus: RS845 5-Pins(COM, TX0, TX1...